Tweaks for systems, rooms and Do It Yourself (DIY) help. FAQ.
In Reply to: RE: Wiring outlet box posted by jea48 on April 15, 2017 at 07:24:33:
I've been doing this for almost four decades, apparently they've amended the code to allow compression connectors UL listed or approved for the purpose and provide an adequate path for ground. This is rather open ended as it leads to all kinds of problems if not adequately employed. First, there's a maximum length the conduit can be run without a ground installed with variables such as number and size of conductors installed, voltage, amperage, type of conduit etc. If someone is injured or killed and the installation is found inadequately grounded through testing it wouldn't be pretty.
Just as its perfectly fine to use the device (meaning the receptacle) as a means of circuit continuity, IE back stabbing or wrapping the screws, but any electrician worth his salt would tail the wire's first, and not use a compression connector as part of the equipment ground integrity.
Edits: 04/15/17This post is made possible by the generous support of people like you and our sponsors:
Topic - Wiring outlet box - JB Coleman 10:44:13 04/14/17 (22)
- RE: Wiring outlet box - jea48 12:32:16 04/14/17 (21)
- RE: Wiring outlet box - Uncle Mike 16:57:40 04/14/17 (15)
- RE: Wiring outlet box - jea48 18:54:08 04/14/17 (14)
- RE: Wiring outlet box - JB Coleman 08:30:12 04/15/17 (5)
- RE: Wiring outlet box - jea48 09:52:42 04/15/17 (4)
- RE: Wiring outlet box - Uncle Mike 03:40:36 04/15/17 (7)
- RE: Wiring outlet box - jea48 07:20:56 04/15/17 (0)
- RE: Wiring outlet box - Kingshead 05:33:14 04/15/17 (5)
- RE: Wiring outlet box - JB Coleman 15:57:42 04/14/17 (4)